View and Download IDEAL Imax W45 installation and servicing manual online. Imax W45 Boiler pdf manual download. Also for: Imax w60p, Imax w80, Imax. Ideal Imax W45, W60, W80 Control Module Ideal Printed Circuit Boards PCB Fits: Ideal Imax W45,Ideal Imax W60,Ideal Imax W Imax W Ideal Imax W45 Spares, Parts, Fan, Gas Valve, Printed Circuit Boards, Pcb’s, Burners Read more.
|Published (Last):||27 March 2012|
|PDF File Size:||8.97 Mb|
|ePub File Size:||4.14 Mb|
|Price:||Free* [*Free Regsitration Required]|
Installation and Servicing Instructions or as otherwise b. Propane gas consumption is calculated using a calorific value of Any direct connection of a control device not approved by In IE, the installation must be carried out by a Competent Person condensing boilers can be installed either on the and installed in accordance with the current edition of I.
IDEAL COMMERCIAL IMAX WW80 & W45P W80P SPARES |
The boiler must not be fitted outside. Should these conditions not apply either lower the pump position or raise the cistern System above the minimum requirement specified by Caradon Ideal System flow to Limited. The isolation valves should be fitted as close to the Jacket side panel Upper gas pipe Jacket front panel assy. Lower gas pipe Thermistor flow or return 12A.
Horizontal flue runs must be inclined at 1. The template shows the positions for the condensate to drain back to the boiler. Care must be taken to ensure the correct holes are drilled. It is not necessary to hold the boiler at an angle to engage the wall mounting plate.
A comprehensive range imaxx flue kits are available from If elbows are to be used, then the equivalent length of that Caradon Ideal Limited.
IDEAL imax W45 Installation And Servicing Manual
Examples of horizontal and vertical fitting see page 17 must be subtracted from the maximum concentric, twin pipe and open flue options are ikax flue extensions allowed for that flue option. Horizontal flue runs must be angled down between 1. For this lengths if required.
When cutting a duct ensure it is square by reason it is recommended that a support bracket is used for marking the length all the way around and only cut back the every 1m of extension pipe. For this reason vertical termination is recommended, and in any case, terminal positions which could cause problems should where possible be avoided.
Particular iddal should be taken in the case of large multiple boiler installations, and complying with the requirements of the Clean Air Act. In installations where the heat load is greater than the boiler capacity idea ideal solution is to use multiple boiler arrangements. The ideal way to control a multiple boiler installation is with our modulating sequencer See below a typical installation with our modulating sequencer kit.
The pipe size from the condensate trap is 25mm. The routing of the drain must be made to allow a minimum fall of 1 in 20 away from the boiler, throughout its length. Standby Mode S t b y The standby mode will be shown after start up or reset of the boiler control module. If no buttons are pressed for 20 minutes the display will automatically be set to standby mode.
The dot after the 1st right digit will be flashing indicating the boiler is in ‘info’ mode. If parameter changes jmax required with the optional kits then further instructions ieal provided with them. System pump maximum load vac 1 amp connect via Permanent a relay for greater main supply currents Frost Stat This system will provide heating umax one zone only at a time with If all zones are fitted with individual zone valves a hydraulic bypass will be required to allow pump overrun.
See page 6 DHW priority. The whole of the gas installation, including the meter, 1. Checks to ensure electrical safety should be carried out by a competent person. If not proceed to 4. Refer to Frames 57, 58, 59, 60, 61, 62, 63 and 64 for guidance.
Caradon Ideal Limited does not accept any liability resulting from the use of unauthorised parts or the repair and servicing odeal. Remove and clean the burner. Refer to Frames 57 and 59 or of appliances not carried out in accordance with the Company’s recommendations and specifications.
Remove the jacket front imas, Refer to Frame Disconnect the electrical connections from the gas valve. Disconnect the electrical connection from the fan.
Remove the jacket front panel. Refer to Frame Remove fan, burner and gas valve assembly. The burner can now be removed. The burner can be cleaned using a soft brush, but Gasket Ribbed only on the back face. Unscrew the nut and disconnect the flexible idexl. Unscrew the nut and remove the condensate trap. Remove the nut and plug from the condensate trap and flush out with water.
Reassemble in reverse order ensuring the condensate trap is full of water before firing. Check for gas soundness. Only valves supplied by Caradon Ideal Limited should be used, as these are factory preset and require no adjustment.
Iax should now be made to Frame 52 to check the gas rate. Re-assemble in reverse order using the new seals and gaskets as imxx. Only Venturi’s supplied by Caradon Ideal Limited should be used as these are factory preset and require no adjustment.
Lower the controls fascia. It is possible to measure the ionisation current with a voltmeter set at VDC. Unscrew the nut retaining the capillary from the self sealing fitting. Unscrew the two screws from the pressure gauge bracket and withdraw the unit ideall the boiler.
Disconnect the transformer connection jmax the boiler control module. Remove the four transformer mounting screws. Reassemble in reverse order.
Imax W45 | AK Gas Appliance & Spares Ltd
Instructions for the British Gas Multimeter or other similar commercially available meter. When replacing any part on this appliance use only spare parts that you can be assured conform to the safety and performance specification that we require.
Do not use reconditioned or iveal parts that have not been clearly authorised by Ideal boilers. Technical Training The Ideal Boilers Technical Training Centre offers a series of first class training courses for domestic, commercial and industrial heating installers, engineers and system specifiers. For details of courses please ring: Also See for imax W45 User manual – 8 pages.
Page of 56 Go.
Idesl of Contents Add to my manuals Add. Performance Data Installation and Servicing Instructions or as otherwise b. Flue Installation Caradon Ideal Limited. Page 8 Should these conditions not apply either lower the pump position or raise the cistern System above the minimum requirement specified by Caradon Ideal System flow to Limited. Flue Kits A comprehensive range of flue kits are available from If elbows are to be used, then the equivalent length of idewl Caradon Ideal Limited.
Boiler Frame And Header Kits In installations where the heat load is greater than the boiler capacity an ideal solution is to iax multiple boiler arrangements.
Servicing If not proceed to 4. Gas Valve Replacement 9. Short List Of Parts When replacing any part on this appliance use only spare parts that you can be assured conform to the safety and idal specification that we require. Page 56 Technical Training The Ideal Boilers Technical Training Centre offers a series of first class training courses for domestic, commercial and industrial heating installers, engineers and system specifiers.
This manual also for: Imax w60pImax w80Imax w45pImax w80pImax w Comments to this Manuals Your Name. Enter text from picture: By pressing ‘print’ button you will print only current page.
To print the manual completely, please, download it. Don’t show me this message again. Got it, continue to print. Don’t have an account?